The incinerator will have chimney, castable top quality refractory cellular lining in addition to burner shell, perforated blind for the main in addition to additional combustion chambers and air blood circulation system.
The burner shall likewise have the following:-.
– Manhole cover complete with a gasket.
– Ash door.
– Fully wired control panel
The bulk oil storage tank shall have a capacity of 10,200 litres and be placed at 0.5 m above ground on a firm concrete cradle, complete with the following:-.
– Dip stick.
Vi) Image electric protective mobile as fire failing tool.
The controls shall be mounted on appropriate control panel to be mounted in a position easy to review and manage from the charging side of the incinerator.
The control board will be generated from anodized, 16SWG, light steel sheet.
The daily oil tank of capacity 1,800 litres in addition to measurement 1220x1220x1220mm pressed steel tank top shall be placed 2.5 metres high above finished floor level on a steel rack, strongly secured on the ground and also the steel participants to be bolted. The oil container shall have an oil level index, availability manhole, washout, overflow, inlet in addition to outlets connections and gateway valves.
The adjoining strand of 50mm size between both storage tanks will be class ‘C’ black mild steel pipe, complete with a 50mm diameter filter. The burner fuel supply pipe in the daily container will be a 25mm size class ‘C’ black mild steel.
The sticking to will additionally be supplied.
– FD fan.
Iii) Re-start after temporary electrical supply failing.
– Pressure in addition to temperature level assesses.
– Temperature level indication gadgets.
– Oil level sign.
– Primary and secondary heaters and also fans.
Iv) Favorable safety and security lock-out as an example of fire failing from whatever reason.
– Air ductwork full with air dampers.
– Gain access to ladder to the top of the storage tank.
– Air vent pipe.
V) Red signal light on control board to indicate security and safety closed out.
– Finishing of the container with at least 2No. Layers of bituminous paint.
– home heating faucet across the heater supply pipe, 25mm size
The heater supply pipe will have 25mm thick fiber glass insulation and perform with gauge 20SWG galvanised steel sheet.
The tenderer will give all the required controls for appropriate safety and also acceptable working of the installment.
The heater shall be acceptable for 35 sec redwood No. 1 scale gas oil. It’ll be robust in building and construction and be produced in celebrities iron or other appropriate products full with placing plates. It needs to be quickly mountable and also demountable for convenience of cleansing and upkeep. The heater shall have a suitable supply of oil that will easily stir up in addition to burn in a safe way. Adequate supply will be offered to protect against any solid thing in the oil, or any type of issue that may divide out from the oil from damaging any parts or chocking of any sort of orifices or shutoffs. The free filtering system location should be sufficient to be certain that the filter doesn’t need dismantling for cleaning up more often than annually. The burner will have fire advice by photo-electric mobile with concurrent sequence controller for automated start up, running and shut-down of the burner.
The burner shall have all the essential controls e.g.Solenoid shutoffs, ignition controls, picture electrical cell gas safety and safety controls, low pressure fuel supply cut-off etc..
The heater will satisfy BS 799: component 3 as well as 6 1981 or any other pertinent British standard.The burner shall be as NU-WAY models or equivalent and also approved.
The incinerator shall operate in an automatic manner with all the required controls. These controls are to include security elements such as fire neglecting unit, pilot lights, integrates, beginners, overload contactors, ON as well as OFF switches for heaters and also followers, combustion chamber temperature signs for main and also second chambers etc..
I) Electric ignition button ‘ON’ before the oil is supplied.